What is a municipal backup or emergency water supply?
uninterrupted water supply undeterred by the availability of municipal water.
In the event of a drop in municipal water pressure, a municipal pipe burst or a municipally imposed water cut, our pump will automatically wakeup and deliver stored water to the home or building. When municipal supply is restored the backup supply will revert to municipal source. Cross-over from one supply to the next is seamless.
The municipal backup/emergency water supply comes with three settings.
- Setting 1 allows only municipal water into the building/home directly, bypassing the pump.
- Setting 2 allows only stored tank water to enter the building/home via the pump. The water in the tank is automatically topped up by municipal supply when available.
- Setting 3, the default position, allows the system to sense when there is an issue with municipal supply. The home/building will receive direct municipal supply provided there is sufficient supply pressure. Should the pressure drop the pump will automatically wake up and supplement or replace the municipal supply. Once the municipal supply has normalised the pump will revert to sleep mode.
What to bear in mind when installing a Backup / Emergency water supply?
- The minimum water storage capacity required.
- The required duration of expected water outage.
- The operating pressure and flow rate required for pump selection.
- Water quality needs and filtration.
- When water is called for and insignificant municipal water is available.
- During the weekly maintenance cycle. (Idle pump protection)
When there is no demand (water use) the pump will remain in sleep mode.
- Water storage tanks should be flushed.
- Replace the batteries of the Idle pump protection mechanism
- Clean out the water filter (if fitted)
- Test all valves
- Recalibrate start-up and shut-off settings
- Re-pressurise expansion vessels
- Inspect system for leaks